CUSTOMER SPECIAL MANUFACTURE
This system was designed for a 3 zone water mist deluge system
The system was put into suction lift despite being positive head, this protects the pump seals if a discharge occurs and the tank hasn't refilled
The system was tested by the client setting fire to his own waste recycling plant.
It was fitted with a relief valve and performed its own auto weekly test
Power came from a generator, the Grifen pump system took a signal from flame detectors, switched on the generator, then time delayed the pump.
A backup system was installed in the cabinet allowing the same starting effect even without the PLC having power
Xcell Misting asked us to provide them something for Christmas.
A space sensitive water mist system has been installed over the Christmas period to protect Santas grotto.
Grifen sprinkler solutions provided a low pressure water mist pump with auto weekly testing and a modified control system.
A 2 head water mist system has been installed with the water supply neatly designed into a tree trunk.
If you have any systems that require special design please contact us
A mobile demonstration unit was built to demonstrate the NXT valve set. A 4 bar pump was used feeding the valeset and sprinkler head. A recirculating sealed water system enabled all the alarms to be tested while the valve was tripped. A Polycarbonate cover enclosed the valve assembly while a high pressure LED was machined into the chamber allowing customers to view the gauges and the internal workings of the valve.